Energy and Environmental
The William Gates building aims to be an energy efficient building.
To optimise energy efficiency, Building Services request that, where possible, users of the WGB refrain from opening windows. If you do need to open your office window, please ensure that your door is kept closed whilst it is open. Please do not leave your window open overnight, or while the office is not in use.
Where possible, use the climate control dial in your room to control the temperature. If you require any further information, please contact Building Services, who will be happy to discuss this issue and answer any questions you may have.
Offices are supplied with fresh air through round metal vents in the floor. Air leaves an office via a rectangular hole on the wall leading to the corridor ceiling void. Air that has passed through an office leaves the building and is not recirculated (except perhaps when the outside temperature is very low). The heat of the outgoing air is recycled through a heat exchanger.
Air flow can be adjusted per building section, as well as in individual floor vents. If you believe that any adjustments are necessary, contact building-services.
Most offices have no individual heating mechanism; a few corner rooms have wall-mounted electric heaters. The air pumped into the floor space is heated in a central machine room to a comfortable temperature (21 °C). Your window and outside office walls are highly insulated. The room temperature depends mainly on
- the temperature and flow rate of air from the floor vents
- power dissipated by electrical devices (computers, lamps)
- solar gain
- the setting of the cooling thermostat
If you have problems with the room temperature, please do not bring in your own heater, get in touch with building-services to discuss the problem.
Each office has a large radiator ("chilled beam") along the wall by the door, which is suspended from the ceiling and covered with a white box. It is connected via a thermostatic valve to the building's chilled water system. This radiator can only cool, not heat the room. It is mainly intended for use in rooms with a large number of computers or where there is too much solar gain over the summer months.
The amount of chilled water flowing through the radiator is controlled by the adjustable thermostat that is located next to the door and light switch. Its settings are:
|5||chilled water flows if room > ~28 °C||warmest setting|
|4||chilled water flows if room > ~24 °C||recommended|
|3||chilled water flows if room > ~20 °C|
|2||chilled water flows if room > ~16 °C||coolest useful setting|
|1||chilled water flows if room > ~12 °C||below water temperature|
|*||chilled water flows if room > ~7 °C||below water temperature|
|0||chilled water flows always||only for testing|
With electrical heating: In rooms that have an electrical heater installed, make sure that the cooling thermostat is closed by setting it to 5 (red marking) when the electrical heater is on. This is to avoid heating and cooling simultaneously and thereby wasting a lot of energy.
Winter heating:Building Services have found that we can provide extra background heat from the Chilled Beams in the Winter, in a reversal of the way in which the Chilled Beams work during the Summer. An e-mail is sent out to the building-users list to let you know that the beams are running warm and that those who wish to take advantage of any extra heating can open the Oventrop Valve or move the control over to the blue setting. Instead of running at 14-16 degrees the beams run at 20-22 degrees during the winter months now. Don't forget to return the valve to its usual setting during the Summer.
Details: The thermostat appears to be an inverted (cold water) version of the oventrop Uni FH with remote control. The above approximate temperatures come from the manufacturer's installation instructions. The dots between numbers 2 and 4 correspond to a temperature difference of 1 °C.
The ceiling lights are equipped with a light sensor located in a small white cylinder at one end of the fitting. They can be adjusted such that the reflected light level seen by the downward-looking phototransistor remains roughly constant. A correctly adjusted sensor helps to save energy. If you believe that your lamp needs adjustment, please contact building-services. If the light malfunctions, the electronic ballast may have to be replaced (we had a series of early failures with these).
- If the lights are on, using the override will turn the lights off permanently until the override button is pressed again.
- If the lights are off (because of the ambient light), use the override to turn the lights on. The lights will remain on until the occupancy period is over.
In the interests of energy efficiency we aim to keep windows closed throughout the building. Open windows increase the heating or cooling demands of the building (provided by gas and electricity). Rising energy costs make it even more critical to ensure that the building is running efficiently.
All windows are equipped with blinds. Where these are not sufficient to protect a room user’s eyes from direct sunlight during some hours of the day, a second, opaque, blind can be installed. Contact Building Services if you need one.
If your room is too hot or too cold, then please let Building Services know so we can adjust the ventilation in your room to your needs.
Why windows should remain closed
The reason why we like to keep windows closed at the William Gates Building is to conserve energy. The Building Mangement System, which controls the climate in the Building, helps with this aim:
- warm air is blown into your room via the floor vents
- cool air is generated by use of the chilled beam control (Oventrop valve) on the wall next to the light switch in your room
- both of these are adjustable
With these control systems in place, when a window is open for long periods of time, while the building is heating in the winter, or cooling in the summer, would lead to a huge waste of energy.
The Building Management System (BMS) is also adversely affected by the false indications given by the temperature change taking place when a window or outside door is left open. Such false indications of temperature can change the settings for heating/cooling for up to three working days.
A large fraction of the energy consumed in our building powers our IT infrastructure. Therefore, where possible, computing infrastructure should be turned off when not in use.
In particular, desk computers should be switched off or sent into a hibernation mode when not used (especially overnight), and their displays switched off. Avoid animated screen savers. If you prefer to leave your computer on to access it remotely, please consider the following alternatives:
- Many PCs can now be remotely switched on as needed, via a web interface.
- Most facilities of your desk computer are also available via our timesharing servers.
The sys-admin wiki features an energy-saving page with more detailed suggestions.
As of April 2011, all waste discarded by the Computer Laboratory is brought to a central recycling site, where it will be sorted.
- Paper can be discarded in collection points next to the printers, but can also be disposed of in normal office bins.
- Glass jars and bottles, cardboard and any general waste can all go into office bins.
- Soft-drink cans and shredded paper will be collected in the same way but with a clear plastic liner in the bin.
- Food waste must be separated and put into the correct bin in the kitchens.
- Batteries, toner, IT equipment, and light bulbs are collected separately at Stores (GW03).
- Estate Management: What you can do